XV INTERNATIONAL TRADE FAIR POWER ENGINEERING FOR INDUSTRY 2017
7-9 November, STC ENPASELECTRO took part in XV INTERNATIONAL TRADE FAIR POWER ENGINEERING FOR INDUSTRY 2017 that took place in the International Exhibition Center (Kyiv).
Works on Kyivska HPP
The specialists of “STC Enpaselectro” carried out reconstruction of the relay protection systems of G13-G16 generators and the T4 transformer of Kyivska HPP Unit №4.
The scope of work included:
- installation of new MiCOM P343 protection terminals on generators G13, G14, G15, G16;
- installation of new MiCOM P634 protection terminals on the Unit №4;
- installation of new MiCOM P139 protection terminals in 6,3kV indoor switchyard bays of Unit №4;
- installation of additional current transformers on the line terminals of the generators G13, G14, G15, G16;
- cabling works;
- commissioning works.
After performing of startup tests, on 17 November 2017 the Unit №4 consisted of four hydrounits was commissioned.
Works on Dniester HPP
At the Dniester HPP, the engineers of the relay protection and automation department of “STC Enpaselectro” together with “Energopartner Engineering” and the station personnel carried out installation, commissioning works, performed reliability run and commissioned a new panel of backup protection of the Unit №3, breaker failure protection and automation of Circuit breaker-52, based on SIEMENS 7SJ804.
The specialists of STC Enpaselectro Ltd. fulfilled the reconstruction of the electrical protection systems of the G1-G4 generators and the T1 transformer of Block No. 1 of the Kiev HPP
Supervisory audit of quality management system
On August 21-22, 2017, the external audit was conducted at STC ENPASELECTRO Ltd as part of the annual verification of the implemented QMS for compliance with the requirements of the international quality management standard ISO 9001:2008.
Agreement with Consortium "Scientific-Production Association" Ukrgidroenergobud" for performance of works on reconstruction of the auxiliary systems of Kaniv HPP Units №4 and №5
STC ENPASELECTRO signed an agreement with Consortium "Scientific-Production Association" Ukrgidroenergobud" for performance of design, installation and commissioning works...
Pre-bid Meeting and Site Visits under ICB: Package UE/3 of PTP-2
As part of the provision of consulting services under ICB: Package UE/3 “Installation and connection of reactive power compensation devices for five 220-330 kV substations” of Second Power Transmission Project specialists of STC ENPASELECTRO...
Commissioning works at Kanivska HPP 330 and 110 kV outdoor switchgears
Specialists of STC ENPASELECTRO together with specialists of EMERSON company completed the commissioning works of the Kanivska HPP 110/330 kV outdoor switchgear control system.
Controllers of 110 kV outdoor switchgear and 330 kV outdoor switchgear were commissioned.
Kanivska HPP unit G-9 was connected to the grid
24 March 2017 - After successful commissioning tests by the specialists of STC ENPASELEKTRO together with the specialists of Emerson company and the electrical personnel of Kanivska HPP the unit G-9 was connected to the grid.
Kanivska HPP units G-10 and G-11 were connected to the grid
14 March 2017 - After successful commissioning tests by the specialists of STC ENPASELEKTRO together with the representatives of Emerson company and the personnel of Kanivska HPP the unit G-10 was connected to the grid.
17 March 2017 - After successful commissioning tests by the specialists of STC ENPASELEKTRO together with the representatives of Emerson company and the personnel of Kanivska HPP the unit G-11 was connected to the grid.
Commissioning works at the Kanivska HPP
The specialists of STC ENPASELECTRO together with the engineers of "Emerson" completed the commissioning works of "Ovation" automatic control systems of G-9...G-12 hydrounits controllers and Unit №3.
Meeting of the Ukrainian National Committee of CIGRE
STC ENPASELECTRO took part in the meeting of the Ukrainian National Committee of CIGRE
Operating test of Dniestrovska HPSPP hydrounit-1
STC ENPASELECTRO specialists together with the engineers of AEG company (Germany), performed operating test of Dniestrovska HPSPP hydrounit-1 runned from static frequency converter №2 (SFC-2).
The algorithms were tested and hydrounit start-up operation in synchronous capacitor and pump modes were performed.
Commissioning of SFC-2 will improve the reliability of the HPSPP due to reservation of functions of previously installed SFC-1.
Meeting on reconstruction of SS 330 kV Brovarska
Meeting concerning the terms of scope of works on substation reconstruction, including the installation of AT-3 was held at SS Brovarska together with representatives of the NPC "Ukrenergo" Kyivsky MES and substation personnel.
The purpose of the meeting was:
Upgrade of the control system of Dniestrovska HPSPP GIS-330 kV
STC ENPASELECTRO specialists upgraded the control system of GIS-330 kV Dniestrovska HPSPP. New version of the software Ovation 3.5.1 was installed, a modification is made to mnemonic scheme, alarm and signal system, сontrol test from main board workstations of switching devices of GIS-330 was performed.
Design works of SAS cabinets
Dnieprovska power system. Substation 330 kV "Dniepro-Donbas" and substation 330 kV "Kirovska". Works on design of SAS cabinets were performed by engineers of STC ENPASELECTRO.
STC ENPASELECTRO Ltd.
Sending the warmest hearty wishes of
Merry Christmas and Happy 2017 New Year!
Let coming year bring you success and new business achievements.
Wish you prosperous, stable and harmonious New Year!
Wish you and your relatives good health and performance of all your dreams!